Larry, I got it setup the other day - no problems. Thank you again.
DGD, Correct, 50% discharge before the inverters shutdown - if I set it higher I am afraid that a heavy load will draw the battery voltage below the threshold and falsely trigger a shutdown. I am not too worried about it because I think this will be extremely infrequent. Its is a new system so I don't have alot of history but the lowest we have seen in the last two weeks was 22% discharged - this was with snow sitting on one of the arrays and while it was snowing for two days. Even on cloudy days I am up to 100 SOC by 10:30 or 11am unless I have heavy loads on the inverters. Rolls claims the batteries will go 1400 cycles at 50% DOD (see attachment), which based on the current limited data I don't think we will see in a 10 year period that I am hoping to get out of the batteries. What do you think?
Mike, I have been observing that too. It is amazing that the bank comes up so quickly in the morning - even without direct sunlight. It is easy to picture your scenario after watching the charge characteristics. - So, I am glad I got it setup to max at 130 amps.